Procond electronic board replacement for Honeywell
Honeywell, which produced control boards for DAKON DUA boilers has already stopped production and sales of PROCOND boards (white).
ATTENTION!!! Now these boards replace the new el. Honeywell boards (green).
Clear table of compensation
|Boiler model||Board name||Cat.No.||Label||Board name||Cat.No.||Label|
|DUA 28BT||Procond BT||87381014420||Honeywell BT||87381014410||SMD0171C|
|DUA 24CT, 24RT, 30CT||Procond CT||87381014070||SMD0155C||Honeywell CT||87381016630||SMD0151C|
|DUA 24CK, 24RK, 30CK||Procond CK||87381013700||SMD0145C||Honeywell CK||87381013690||SMD0141C|
|DUA 28BK||Procond BK||87381014400||Honeywell BK||87381014390||SMD0171C|
Power exchange Procond boards for Honeywell for model DAKON DUA BT
- The control automation can be replaced by Honeywell 87381014410 automation for DUA BT boilers (turbo with storage tank). The automatic control system must cooperate with the DHW control thermostat with capillary 87381014380 . In addition, you will need the MAN0400C / 70330140 control thermostat operation switch knob. Unical only supplies the buttons in a set. The order code for the kit is 95000365 .
- DUA BT boilers can continue to be operated where Procond automation was with the TNC storage tank sensor 87381017950 . To replace the automation, the TNC must remove the storage tank sensor and replace it with a DHW control thermostat with an operating switch knob (crescent).
- More also herePDF .